Payment & Shipping Terms:
|Item:||Fixed Type Innovating Aerosol Extinguishing Systems Eco-friendly Clean Agent||Extinguishing Device Weight(Kg):||6.8|
|Agent Quantity(Kg):||3.5||Protected Volume (m³):||125m³|
|MSDS:||We Have For Export||Discharge Time(s):||≤19|
|Typical Applications:||Underground Pipeline/ Control Room/ Equipment Room/Storage Room||Model:||Fireless 125|
aerosol fire system,
aerosol fire protection
Fixed Type Innovating Aerosol Extinguishing Systems Eco-friendly Clean Agent
Brief requirements of Aerosol Extinguishing Systems according to GA499.1-2010
Fireless 125 technical parameter:
|Overall dimensions(mm)||240( diameter)X126(height)|
|Extinguishing device weight(Kg)||6.8|
|Discharge times)||≤ 19|
FAQ for technical terms
Answer: no, it doesn’t .
Answer:Represents the unsealing degree of the enclosed space, and its value is the ratio of the unclosed open area in the enclosed space to the total surface area, expressed as a percentage.
Answer:The mass of an aerosol agent required to extinguish a fire in unit volume, g/m³.
Answer:The time when the fire extinguishing device receives the starting signal and the nozzle begins to spew hot gas sol extinguishing agent.
Answer:The time from the beginning discharging aerosol to discharging stopped.
Answer:During the process of discharge heat aerosol fire extinguishing agent, the outlet temperature is where 5 meters away from nozzle.
Answer:Yes, it’s medium or device installed in a fire extinguishing device to effectively reduce the temperature of a hot gas aerosol extinguishing agent before it passes through the nozzle.
data centers/ UPS/ ESP/ museums/ warehouses/ electric cabinets/ generator rooms panels/ engine rooms/ different transportation vehicles