Payment & Shipping Terms:
|Item:||Green And New Technology Portable Extinguisher For Electrical Cabinet Fires||Type:||Green And New Technology Portable Extinguisher|
|Agent Quantity:||10g||Application:||For Electrical Cabinet Fires|
|Executive Standard:||GA499.1-2010, GJB150A-2009||Extinguishing Fire Class:||A,B,C,E, (k)|
aerosol fire extinguisher,
aerosol extinguishing system
Green And New Technology Portable Extinguisher For Electrical Cabinet Fires
1. Brand Name: FireLess
2. Model Number:FireLess 1.0+
3.Outside diameter:Φ85X26(H) (mm)
4.Color: Chinese red
5. Main agent content: potassium nitrates
FireLess 1.0+ Green And New Technology Portable Extinguisher For Electrical Cabinet Fires
|Outside diameter (mm)||Φ85X26(H)|
|Extinguishing device weight(g)||40|
Heat- sensitive wire
|Start-up current(mA, DC)||≥700|
|Safety current(mA, DC)||≤150|
|Electric start-up lines length (mm)||50~500(Customized)|
|Period of validity (year)||10|
|Compatibility||Can be used with existing fire alarm system|
1. prompt response in 24 hours once get the inquiry
2. Professional reply and advice for customer questions
3. Best and most professional proposal will be provided according to customer requirement.
4. Good after-sale service. If customer meet any problems, quick reply and prompt assistance to help solve the problems.
The fire causes in the electrical cabinet
The main causes of electrical fires in electrical cabinets for power distribution cabinets or other purposes are: short circuit, overload, poor contact, overheating of electric appliances, ignition of combustibles, static electricity, lightning strikes, mishandling, etc., in which short circuit and overload are the main reasons. Wire and cable fires have the largest proportion. In the event of a fire, the equipment will be costly and, in severe cases, will cause adverse social impacts. If electrical cabinet fires can be extinguished in the shortest time and early stage, the impacts can be minimized.
The importance of fire protection for the electrical cabinet
The electrical cabinet plays an important role in various fields. Electrical components for electrical energy distribution are integrated into the electrical cabinet. Its function is to distribute and control the electrical equipment, and provide power-off protection when there is overload, short circuit and leakage on the circuit.
Why FireLess 1.0 is the better selection for small electrical cabinets
When choosing a fire extinguishing device, we have to compare the advantages and disadvantages of various fire extinguishing devices. Firstly, the fire extinguishers you choose can be used for extinguishing energized equipment fires. So the foam or water fire extinguishing devices are not suitable. They will cause an electric shock to people. Secondly, the fire extinguishing agent dry powder fire extinguisher will damage the protected objects and many residues left, repairing work and cleanup will be more difficult.