Payment & Shipping Terms:
|Item:||Fixed Aerosol Fire Extinguishing Systems Modular And Automatic Condensed Aerosol Type||Extinguishing Device Weight(Kg):||5.3/3.4kg|
|Agent Quantity(Kg):||2.8/1.4kg||Protected Volume (m³):||100/ 50m³|
|Main Components:||Mounting Brackets, Tank Of Fire Extinguishing Device, Electric Starter||Thermal Clearance Of Aerosol (m):||When400℃≤0.14 When 200℃≤0.28 When 75℃≤0.75|
|Installation Method:||Fixed By Bolting||Main Material Of Device:||Carbon Steel|
aerosol based fire suppression system,
aerosol fire extinguishing generators
Condensed Aerosol Fire Suppression System For Vehicle Engine Room Fire Protection
|Product model||FireLess 50||FireLess 100|
|Activation mode||Electric start||Electric start|
|Operation condition temperature||-50℃~+95℃||-50℃~+95℃|
|Activation current||700mA, DC||700mA, DC|
|Installation method||Fixed by bolting||Fixed by bolting|
|Main material of device||Carbon steel||Carbon steel|
The product characteristics
1. Extremely effective extinguishing agent, developed from military technology
2. Small space occupied because of compact design
3. Non toxic, ecologically safe and environmentally friendly ( Global Warming Potential=0, Ozone Depletion Potential=0,)
4. Uniquely easy to install and operate
5. Non-pressurized and no need of biding pipes
6. Low maintenance cost and labor cost
7. Widely applications, hazard of Class A, B, C, E fires can be controlled and extinguished,
The mostly common fire protection system
Dry Powder Fire Extinguishers
Dry powder fire extinguishers are widely used to extinguish fires in your home, office, factories, etc. They cover class A, B and C fires. But when it killed fires, there will have much residues, it may cause another damage to the protected objects and not easy to clean.
The main differences between a fire sprinkler and fire suppression systems are how they extinguish fires and when each system would be ideal to use.
Sprinkler fire extinguishing system
The sprinkler fire suppression systems need detection and alarming system to detect heat, smoke, or both and make the sprinkler fire suppression systems activated. Fire sprinkler systems use water to extinguish or control flames and minimize the fire spread. But it is limited to the water source and location and need to install pipes before. So the cost is higher and adaptability is not very good.
Aerosol fire extinguishing device
Aerosol fire extinguishing device suppress fires by a hot condensed aerosol which is transferred from a solid chemical forming compound, the main component are potassium nitrates. It is activated by electricity or mechanical temperature sensing self-start. Smaller volume, lighter weight, bigger protect space. Mostly can used for many filed like energy, vehicles, marine, etc.